Genset Diesel Generator
Cummins Diesel Generators
Perkins Diesel Generator
Small Gasoline Powered Generator
Small Diesel Generator
Marine Diesel Engines
Deep Sea Control Panel
CAT-parts Generator Parts
Cummins Generator Parts
Uninterruptible Power Supply
Atlas Copco Spare Parts
FG Wilson Generator Parts
Magnetic Door Lock
FG Wilson Control Panel
Automatic Voltage Regulators
Industrial Hand Cleaner
K.S. LIMYour genset and ATS are working well. I have given your name and email to a friend who will be building a hotel in Palawan. Thanks,
Waleed-EgyptThanks always giving me good products. thanks for your effort you done before. your firend from Egypt.
Akakulubelwa Mwiyakui-ZambiaI must confess you have a brilliant customer relations skills and i am learning from you. I tell you if you want to see how beautiful Zambia in Africa
Two Phase Automatic Voltage Regulators
|Place of Origin||China OEM and UK|
|Minimum Order Quantity||1-5 pieces|
|Packaging Details||Standard plywood and wood package.the actual package size against goods size and handle requires.|
|Delivery Time||one weeks on receipt of official sales contract|
|Payment Terms||L/C,D/P,D/A, Alipay, West Union, TT. Cash,Paypal|
|Supply Ability||500 pieces per Month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
avr automatic voltage regulators,
automatic voltage regulator circuit
MX341 is a two phase sensed Automatic Voltage Regulator and forms part of the excitation system for a brush-less generator. Excitation power is derived from a three-phase permanent magnet generator (PMG), to isolate the AVR control circuits from the effects of non-linear loads and to reduce radio frequency interference on the generator terminals.
Sustained generator short circuit current is another feature of the PMG system.
The AVR senses the voltage in the main generator winding and controls the power fed to the exciter stator and hence the main rotor to maintain the generator output voltage within the specified limits, compensating for load, speed, temperature and power factor of the generator.
Soft start circuitry is included to provide a smooth controlled build up of generator output voltage. A frequency measuring circuit continually monitors the shaft speed of the generator and provides under-speed protection of the excitation system by reducing the generator output voltage proportionally with speed below a pre-settable threshold. A further enhancement of this feature is an adjustable volts per Hertz slope to improve engine recovery time on turbo charged engines.
Soft start circuitry is included to provide a smooth controlled build up of generator output voltage. Uncontrolled excitation is limited to a safe period by internal shutdown of the AVR output device. This condition remains latched until the generator has stopped.
Provision is made for the connection of a remote voltage trimmer, allowing the user fine control of the generator's output. An analogue input is provided allowing connection to a Newage Power Factor controller or other external devices with compatible output.
The AVR has the facility for droop CT connection, to allow parallel running with other similarly equipped generators.